PEIDE has established a long-term relationship with major banks.The debugging and installation of chemical dosing systems which purchased by Bank of communications Changzhou branch have been accomplished last month.Another good news,two sets of condenser rubber ball cleaning devices which orderd by Bank of communications Shanghai branch have been debugged and installed successfully at this month.Many banks are our loyal customers,such as HSBC Shanghai branch.They satisfied with our products very much.Successive order is greatest trust and encouragement to us.The two sets of condenser rubber ball cleaning devices are used in the condenser of central air conditioning system.
The condenser rubber ball cleaning device can solve the condenser corrosion and scaling problems,optimize heat exchange efficiency,maintain the cleanness of the condenser tubes and no need manual cleaning.The use of the condenser rubber ball cleaning device can save a lot of cost to the customer.After installing central air conditioner condenser rubber ball cleaning device, the condenser is running with no dirt clean state to host a 300-ton (Input power:200KW) under 5000 hours in the boot cases: power consumption = 200KW ×80% ×host load boot 5000 hours = 800,000 degrees.Suppose 1.0 yuan/kWh tariff calculation,the corresponding cost: 800,000°×1.0 yuan/kWh = 800,000 yuan
Welcome to visit our factory,if you have any question,please contact us.
The installation of condenser rubber ball cleaning device as below:
We supply all kinds of rubber balls.The parameters which provided by the customers can be customized.
The details of rubber balls as below:
The parameter of condenser rubber ball cleaning device as below:
|The model of condenser rubber ball cleaning device||PCE-PD-300-N|
|Appropriate pipe diameter||DN300|
|Injector||Inlet and outlet diameter:DN50
Chamber meterial:carbon steel
Have exhaust system and drainage system
Have adding ball device and collector
|Ball collector||Inlet and outlet diameter:DN300
Chamber meterial:carbon steel
Have maintenance entrance
Have pressure gauge which can display the differential pressure from the strainer
|The description of electric controller||Matching|
|Control method||Automatic time control,Manual control,Failure alarm|
|The sight glass for watching rubber balls||Plexiglass|
|Auto exhaust valve||Copper|
|Electric valve||3 pieces|
|Fittings||Pressure gauge:1 piece
Flow switch：2 pieces
Internal pipeline:PVC,Steel Pipe
Rubber balls(the inner diameter and quantity of copper pipes for condensor should be provided)
The installation chart of condenser rubber ball cleaning device as below:
The installation notice of condenser rubber ball cleaning device as below:
The ball collector should according to the appropriate pipe diameter to connect to outlet pipe of condensor cooling water.The interface flange according to the label to connect.The arrow direction of ball collector and the flow direction are in the same direction.
The inlet and outlet of Injector flange connected to the inlet pipe of condensor cooling water.The inlet and outlet of the inlet pipeline spacing more than 0.5 meters.The inlet should be in front of the outlet pipe.
Set aside not less than 0.6M of maintenance space around the host processor of condenser rubber ball cleaning device.
The connecting pipeline of the ball collector and the condenser rubber ball cleaning device should be vertical and horizontal,to minimize the corners.
In order to prevent the block and scratch of the condenser rubber ball cleaning device,the pipeline which from injector to ball collector and the cover of condenser should not contain iron filings,welding slag,etc.We suggest that you can install a filter at the front of injector.
We also suggest that it should to install filters to the inlet of condensor and add corrodent and fungicide to it.
If you want to get more info of the condenser rubber ball cleaning device,please click here.